PR&CM is a fully accredited Sydney Water Servicing Coordinator. Our projects create value for people and communities, and pave the way for our clients to succeed.
Site Inspection in Austral NSW
As part of our Water Services Coordinator works we attended the site in Austral during the connection of both new sewer and water connection points. We are required to make sure the accredited contractor carries out the works in accordance with Sydney Water specifications. This is a part of the Section 73 process for our client as part of a dual occupancy development with torrens title subdivision.
Surveying Works in West Pennant Hills NSW
As part of our Water Service Coordinator works we attended a site in West Pennant Hills and conducted a survey of the newly constructed sewer main, prior to booking in a major works connection. We wanted to ensure the works are carried out in accordance with our design plan. The project is a subdivision creating three residential lots including demolition.
The project included micro-tunnelling to save some large trees.
Pier Inspection in Gledswood Hills NSW
Staying close to home of our Gregory Hills office!
As part of our Water Service Coordinator works we conducted the pier inspection for a new residential property in Gledswood Hills. We made sure the piers are located the correct distance from a Sydney Water sewer main and that they extend below the zone of influence. This is a part of the building plan approval for our client.
Concrete Encasement Inspection in Albion Park, NSW
As part of our Water Services Coordinator works we conducted a site inspection on the pipe prior to concrete being poured in Albion Park. The items we are interested in are pipe type, pipe integrity, Trench drainage (A.G pipes) installed on either side. Minimum encasement is to be 150mm around the exterior of the pipe, pipe support and pipe braces are to be used. Once satisfied we provided the Sydney Water constructor the go ahead to encase the pipe. This is part of the building plan approval process.
Major Sewer Connection Inspection in Prestons, NSW
As part of our Water Services Coordinator works we conducted a major sewer connection inspection for a site in Prestons. As part of Prestons booming industrial development, we were requested a connection with Sydney Water to connect into an existing Sydney Water sewer manhole. During our inspection, we were required to make sure the constructor applies all safety controls to minimize risk and all documentation needs to be submitted. Once satisfied the constructor is given the go ahead to core drill into the manhole and connect the new DN225 sewer pipe.
Pier Inspection in Tamoor, NSW
Client: Samaro Homes
Description: As part of our Water Services Coordinator works we attended the site and conducted an inspection on the piers prior to pouring concrete. We were required to confirm onsite the location of Sydney Water assets and subsequently ensure the new piers are correctly placed and are drilled below the assets zone of influence. If they adhere to Sydney Water’s technical guidelines, we will allow them to proceed with concrete. This is a part of the building plan approval process for our client Samaro Homes.